JMP is excited to announce our new technical HVAC magazine! It is a great resource to get bite-sized educational pieces similar to the content featured in our seminars. Register to have the latest blog sent to your email address.
One of the most important lines on a pump performance curve is the Net Positive Suction Head (NPSH) curve. Discreetly applied either below or above the pump performance and efficiency curves, this single plotted line is the key to avoiding cavitation. Required NPSH or NPSHR for a given pump increases with flow. So, using the pump curve shown in Figure 1, we can see that the NPSHR for this Model 1510 B & G pump with a 8” impeller and 800 GPM and 33 Feet of Total Head is 12 feet of head.